Ми зв'яжемося з вами найближчим часом
Atom 8R - The extension module is designed to control powerful loads using 6 relays with a switching current of 16A. Great for automating electric heating.
Important! During installation and operation, observe the general rules of electrical safety regarding the use of electrical appliances, as well as the requirements of regulations on electrical safety. It is strictly forbidden to disassemble a device to which any conductors are connected!
Important! Although the controller has built-in protection against incorrect power connection, and in this situation will not fail, we recommend that you pay attention to the correct polarity when connecting.
Connect the extension controller to an i3-NET network. Install the end terminators included in the equipment kit at the ends of the bus.
Connect the controlled devices to the outputs. Each output is implemented in the form of a 2-pin connector and is designed to connect conductors with a cross-section up to 2.5 mm2. One of the contacts is marked "OUT". The load is connected according to the type of output.
Examples of connecting loads to Extension 8R are given below
OUT1-OUT6 - relay outputs with switching current up to 16A (active load), designed for switching direct and alternating current loads with a voltage of up to 250V.
Outputs are intended for connecting powerful loads: lighting groups, pumps, fans, electric motors, boilers, electric heating devices.
OUT7-OUT8 - relay outputs with switching current up to 5A (active load), designed for switching direct and alternating current loads with a voltage of up to 250V.
Best suited for controlling low-power loads: thermal heads, low-power LED lamps and lights, devices with dry contact type inputs (garage gates, impulse blinds), intermediate relays, emergency lighting, electric locks.
The device is turned on, but is not visible in the application settings
1. Check the presence of supply voltage on the module2. Check the polarity of the power supply
The load does not turn on or reacts incorrectly
1. Check the correctness and reliability of the connection2. Check if the connected load operates properly