We will contact you shortly.
Important! During installation and operation, observe the general rules of electrical safety regarding the use of electrical appliances, as well as the requirements of regulations on electrical safety. It is strictly forbidden to disassemble a device to which any conductors are connected!
Important! Although the controller has built-in protection against incorrect power connection, and in this situation will not fail, we recommend that you pay attention to the correct polarity when connecting.
Connect the extension controller to an i3-NET network. Install the end terminators included in the equipment kit at the ends of the bus.
Connect the devices controlled by the module to the outputs. The device has 6 groups of relays: 2 groups of mechanical and 4 groups of electronic AC relays. The common output of mechanical groups is marked COM, and electronic L, and all outputs are numbered. Each group is implemented in the form of a 4-pin connector and is designed for connecting conductors with a cross-section of up to 2.5 mm2.
Examples of connecting loads to Atom R6A12 extension are shown below.
OUT1-OUT6 and OUT13-OUT18 - outputs of solid-state relays designed for noiseless switching of alternating current loads with a voltage of up to 250V and a power of up to 100W per channel.
OUT7-OUT12 - outputs of mechanical relays with switching current up to 5A (active load), designed for switching direct and alternating current loads with a voltage of up to 250V.
Best suited for controlling low-power loads: thermal heads, low-power LED lamps and lights, devices with dry contact type inputs (garage gates, impulse blinds), intermediate relays, emergency lighting, electric locks.
The device is turned on, but is not visible in the application settings
1. Check the presence of supply voltage on the module2. Check the polarity of the power supply
The load does not turn on or reacts incorrectly
1. Check the correctness and reliability of the connection2. Check if the connected load operates properly