We will contact you shortly.
A great solution for completely silent control of AC loads. Allows you to adjust the brightness of lamps and lamps and the speed of rotation of fans or motors.
Important! During installation and operation, observe the general rules of electrical safety regarding the use of electrical appliances, as well as the requirements of regulations on electrical safety. It is strictly forbidden to disassemble a device to which any conductors are connected!
Important! Although the controller has built-in protection against incorrect power connection, and in this situation will not fail, we recommend that you pay attention to the correct polarity when connecting.
Connect the extension controller to an i3-NET network. Install the end terminators included in the equipment kit at the ends of the bus.
Connect the devices controlled by the module to the outputs. The device has 6 groups of solid-state alternating current relays. The common output of each group is marked L, and all outputs are numbered. There are 3 outputs in each group, except for the second group, where there are 2 outputs and 1 N-contact for the operation of a common zero detector for all dimmed outputs. Each group is implemented in the form of a 4-pin connector and is designed for connecting conductors with a cross-section of up to 2.5 mm2.
Examples of connecting loads to the Atom AD8A9 extension module are shown below.
OUT1-OUT5 and OUT15-OUT17 - dimmers for controlling alternating current loads with a supply voltage of 180-250V.
Allows you to control the brightness of lamps and adjust the speed of rotation of fans, pumps and electric motors. The maximum load power for one dimmer channel is 100 W.
OUT6-OUT11 - outputs of solid-state relays designed for noiseless switching of direct and alternating current loads with a voltage of up to 250V and a power of up to 80W per channel.
OUT12-OUT14 - outputs of solid-state relays designed for silent switching of direct and alternating current loads with a voltage of up to 250V and a power of up to 100W per channel.
The device is turned on, but is not visible in the application settings
1. Check the presence of supply voltage on the module2. Check the polarity of the power supply
The load does not turn on or reacts incorrectly
1. Check the correctness and reliability of the connection2. Check if the connected load operates properly